- [Instructor] There's more to sprinkler systems…than just pipe and sprinklers.…Let's start looking at other items,…such as how the fire department can hook…into your water supply.…In this video we're gonna choose…a fire department inlet connector.…We will then run pipe off the connector…and up through our building.…To get started let's jump into AutoCAD.…Go into our fire department drawing.…In your workspace switching,…let's make sure piping is set current.…Let's go to our equipment tab.…
On the very top let's click on mechanical equipment.…In fire protection let's drill in to…where it says fire department inlet connectors.…Let's scroll down to 3-way flush.…Select the top one.…Now select the bottom one.…What's nice is you get a pretty good preview…of what you're able to bring in.…I'm gonna grab the one with the plate on it.…For my elevation, right down here,…let's type in four feet and hit enter.…
Now let's click into our drawing area.…Let's scroll down to this wall here.…Remember we have our snaps turned off.…So let's shift + right-click and select nearest.…
- Externally referencing architecture
- Setting up display configurations
- Adding room tags
- Setting up routing preferences and systems
- Adding piping and connectors
- Adding fire-alarm devices and control panels
- Creating sections
- Merging and refreshing sections
Skill Level Intermediate
Migrating from AutoCAD to Revitwith Paul F. Aubin2h 18m Intermediate
1. Setting Up the Sprinkler
2. Setting Up the Sprinkler Piping
3. Setting Up the Fire Alarm
- Mark as unwatched
- Mark all as unwatched
Are you sure you want to mark all the videos in this course as unwatched?
This will not affect your course history, your reports, or your certificates of completion for this course.Cancel
Take notes with your new membership!
Type in the entry box, then click Enter to save your note.
1:30Press on any video thumbnail to jump immediately to the timecode shown.
Notes are saved with you account but can also be exported as plain text, MS Word, PDF, Google Doc, or Evernote.